- Personal Care
- Food Service
- Top Sellers
Dosages will depend on the characteristics of the make-up water, the permissible cycles of concentration, and at cooling towers rated tonnage versus its operational tonnage.
This product should be fed at a rate of 200 to 400 ppm (25 to 50 ounces per 1000 gallons of cooling water capacity).
It should be fed to maintain a residual molybdate test level of between 1.2 and 2.4 ppm molybdate.
It is recommended that this product should be fed on a continuous basis using a suitable treatment pump and control unit. It may be fed directly from the drum or diluted to a convenient concentration of water. It should be fed to a point in the system where it will be thoroughly mixed and evenly distributed. It should be used in conjunction with an alternating algae cide and bio cide treatment program.
- Scale and corrosion
- Inhibitor for Cooling Towers using Hard Water
- Cooling Towers
Corrosion Inhibitor Corrosion Inhibitor - Tower Treat H - Scale & Corrosion inhibitor for hard water.
This scale and corrosion inhibitor is specifically formulated for open recirculating cooling water systems in areas of high hardness, a high alkalinity scaling waters. It contains a strong calcium carbonate crystal modifier, which prevents calcium carbonate deposition, along with yellow metal protectant. Contains a polymer designed to inhibit scale and deposition in a wide variety of aqueous systems.Related Products$129.16
This liquid steam boiler treatment is a non-phosphate dispersant and scale inhibitor designed for use as a supplement to chelant, carbonate or phosphate treatments. It removes and controls scale.....$134.76
Nitrate Scale Inhibitor Nitrate Scale Inhibitor - Loop Treat Nitro - Borate & nitrate scale & corrosion inhibitor......